INDUSTRIAL SITE, Eaubonne
Gas detection equipment in refrigeration rooms
Detectors should be distributed as close as possible to high-leakage-risk areas and in the bottom part since the monitored gases are heavy ones.
We recommend installing a detector below each group, in the area where leakage risk is highest (valves, seals, moving parts).
The detectors are connected to a central unit which operates according to the measured concentrations using audible and visual alarm devices and through the activation of the ventilation.
Remote alarm transfer is strongly recommended.
Get in touch with us
for any further information.